It depends.Yes. All mailboxes have to be accessible and if that requires ramps, clear floor/ground space, and parking then they must be provided to make the mailboxes accessible.If the oldest mailbox was built prior to the effective date of the FHA, 5/13/91, then it would not be required to comply with the FHA.
If you will look at the exception 3, you will find that only 50% of each use must be accessible. If they are both unisex then there is only one type so only 1 of the 2 (50%) must be accessible. Please note that this exception is applied to bathing rooms but the ADA exception does not apply to bathing … READ MORE
Yes. The ADA covers doors. Doors are required to be operable with 5 Pounds of force maximum and have a closing speed of 5 seconds or greater from fully open to approximately 8” from fully closed. The openers you mentioned are a great substitute. They serve as an equivalent facilitation to the above listed requirements. They come with a very … READ MORE